Mode 5. Cooling
Without exterior condenser or water condenser. The unit’s free cooling system will endeavour to reach the conditions selected by the user as well as keeping to indoor air quality (IAQ) standards. The by-pass valve on the recuperator is used to make the most of outdoor conditions.
With exterior condenser. This optional feature is recommended for facilities in areas with high humidity and high temperatures. It expels excess heat outdoors and feeds cool, dry air into the pool.
As this feature is built into the unit, no additional installation is required.
With water condenser. When temperatures in a pool facility rise above the default temperature, warm air will no longer be fed into it. However, it may still be necessary to dehumidify the air, but as the outdoor air cannot be used to do so the cooling cycle will start to run and instead of condensing the air, both the air and water will be condensed.